;------------------------------------------------------------------------------
; This GSD (General Station Description) is provided by PI C3PG7 "PA Profile".
; This GSD is available for download at PI web server.
; The Profile GSDs cover the common subset of functions of devices of
; a specific PA device type providing interchangeability.
;
; This file describes the device type:
; Liquid analyzer for conductivity measurement
; with 2 Analog Inputs
; Physical layer MBP.
; This file becomes valid with the PA profile version 4.0.
;
; Last modification: 2017-10-20
;------------------------------------------------------------------------------
#Profibus_DP
;Standard definitions, valid for all device types with MBP
GSD_Revision = 5
Vendor_Name = "Profile Process Control Devices"
Revision = "PA 4.x"
Protocol_Ident = 0
Station_Type = 0
FMS_supp = 0
Hardware_Release = "-"
Software_Release = "-"
31.25_supp = 1
45.45_supp = 1
93.75_supp = 1
187.5_supp = 1 ;needed to support spec. network devices
500_supp = 1 ;needed to support spec. network devices
1.5M_supp = 1 ;needed to support spec. network devices
3M_supp = 1 ;needed to support spec. network devices
6M_supp = 1 ;needed to support spec. network devices
12M_supp = 1 ;needed to support spec. network devices
MaxTsdr_31.25 = 100
MaxTsdr_45.45 = 250 ;exception for spec. network devices
MaxTsdr_93.75 = 1000
MaxTsdr_187.5 = 60
MaxTsdr_500 = 100
MaxTsdr_1.5M = 150
MaxTsdr_3M = 250
MaxTsdr_6M = 450
MaxTsdr_12M = 800
Redundancy = 0
Repeater_Ctrl_Sig = 0
24V_Pins = 0
Freeze_Mode_supp = 0
Sync_Mode_supp = 0
Set_Slave_Add_supp = 1
Min_Slave_Intervall = 250
Modular_Station = 1
Slave_Family = 12@Profile4
;end of standard definitions
;Device type specific definitions
Model_Name = "Liquid analyzer conduc. (PhyL 1)"
Ident_Number = 0xB371
Bitmap_Device = "PA_B371n"
Max_Module = 2
Max_Input_Len = 10 ;2*AI(2*5)
Max_Output_Len = 0
Max_Data_Len = 10
Max_Diag_Data_Len = 28
Modul_Offset = 1
Max_User_Prm_Data_Len = 24
Ext_User_Prm_Data_Const(0) = 0x80 ;DPV1 Status 1
Ext_User_Prm_Data_Const(1) = 0x00 ;DPV1 Status 2
Ext_User_Prm_Data_Const(2) = 0x08 ;DPV1 Status 3
;--- Startup parameter of the Physical Block (Slot 0)
PrmText = 1 ;STARTUP_PARAM_VALIDITY
Text(0) = "Ignored"
Text(1) = "Applied"
EndPrmText
ExtUserPrmData = 1 "Startup parameters"
Unsigned8 0 0-1
Prm_Text_Ref = 1
EndExtUserPrmData
Ext_User_Prm_Data_Const(3) = 5,66,0,0,0x00
Ext_User_Prm_Data_Ref(7) = 1 ;STARTUP_PARAM_VALIDITY (Unsigned8)
;--- Startup parameter of the liquid analyzer transducer block - (Slot 1)
PrmText = 2 ;Analysis value units
Text(1552) = "uS/cm"
Text(1302) = "mS/cm"
EndPrmText
ExtUserPrmData = 2 "Unit (conductivity)"
Unsigned16 1552 0-65535
Prm_Text_Ref = 2
EndExtUserPrmData
PrmText = 3 ;Temperature units
Text(1000) = "kelvin"
Text(1001) = "degree Celsius"
Text(1002) = "degree Fahrenheit"
Text(1003) = "degree Rankine"
EndPrmText
ExtUserPrmData = 3 "Unit (temperature)"
Unsigned16 1001 0-65535
Prm_Text_Ref = 3
EndExtUserPrmData
Ext_User_Prm_Data_Const(8) = 8,68,1,0,0x06,0x10,0x03,0xe9
Ext_User_Prm_Data_Ref(12) = 2 ;analysis value unit (Unsigned16)
Ext_User_Prm_Data_Ref(14) = 3 ;temperature unit (Unsigned16)
Prm_Block_Structure_supp = 1
PrmCmd_supp = 1 ;slave supports PrmCmd
Slave_Max_Switch_Over_Time = 20 ;=200 ms
Slave_Redundancy_supp = 1 ;slave is not redundant but can be connected to a flying master
Info_Text = "Liquid analyzer for conductivity measurement with \
PROFIBUS PA (MBP) communication interface."
Ident_Maintenance_supp = 1
;----------- Description of extended DP features: ---------------------
;
DPV1_Slave = 1
C1_Read_Write_supp = 1
C1_Max_Data_Len = 128
C1_Response_Timeout = 1000
C2_Read_Write_supp = 1
C2_Max_Data_Len = 128
C2_Max_Count_Channels = 1
Max_Initiate_PDU_Length = 52
C2_Response_Timeout = 1000
DPV1_Data_Types = 0
WD_Base_1ms_supp = 0
Check_Cfg_Mode = 0
;----------- Description of device related diagnosis: ---------------------
;
Unit_Diag_Bit(16) = "Status appears"
Unit_Diag_Bit(17) = "Status disappears"
Unit_Diag_Bit(35) = "Restart" ;DIA_WARMSTART
Unit_Diag_Bit(36) = "Application reset" ;DIA_COLDSTART
Unit_Diag_Bit(37) = "Maintenance required" ;DIA_MAINTENANCE
Unit_Diag_Bit(40) = "Maintenance alarm" ;DIA_MAINTENANCE_ALARM
Unit_Diag_Bit(41) = "Maintenance demanded" ;DIA_MAINTENANCE_DEMANDED
Unit_Diag_Bit(42) = "Function check" ;DIA_FUNCTION_CHECK
Unit_Diag_Bit(43) = "Out of specification" ;DIA_OUT_OF_SPEC
Unit_Diag_Bit(44) = "Parameter update" ;DIA_UPDATE_EVENT
Unit_Diag_Bit(55) = "Extension available"
;NE107_COMMON
Unit_Diag_Bit(56) = "Sensor element exciter faulty"
Unit_Diag_Bit_Help(56) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(57) = "Error in evaluation electronics"
Unit_Diag_Bit_Help(57) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(58) = "Error in internal energy supply"
Unit_Diag_Bit_Help(58) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(59) = "Error in sensor element"
Unit_Diag_Bit_Help(59) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(60) = "Error in actuator element"
Unit_Diag_Bit_Help(60) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(61) = "Faulty installat e.g. dead space"
Unit_Diag_Bit_Help(61) = "Check installation."
Unit_Diag_Bit(62) = "Parameter setting error"
Unit_Diag_Bit_Help(62) = "Check parameter settings for consistency."
Unit_Diag_Bit(63) = "Signal path broken or short cut"
Unit_Diag_Bit_Help(63) = "Check signal path."
Unit_Diag_Bit(64) = "Overloading"
Unit_Diag_Bit_Help(64) = "Check load."
Unit_Diag_Bit(65) = "Wrong polarity of aux power"
Unit_Diag_Bit_Help(65) = "Check polarity."
Unit_Diag_Bit(66) = "Maximum line length exceeded"
Unit_Diag_Bit_Help(66) = "Check line length."
Unit_Diag_Bit(67) = "Corrosion/abrasion by medium"
Unit_Diag_Bit_Help(67) = "Replacement is recommended."
Unit_Diag_Bit(68) = "Fouling on sensor element"
Unit_Diag_Bit_Help(68) = "Cleaning is recommended."
Unit_Diag_Bit(69) = "Auxil medium missing or insuffic"
Unit_Diag_Bit_Help(69) = "Check auxiliary medium."
Unit_Diag_Bit(70) = "Wear reserve used up (operation)"
Unit_Diag_Bit_Help(70) = "Plan maintenance."
Unit_Diag_Bit(71) = "Wear reserve used up (wear)"
Unit_Diag_Bit_Help(71) = "Plan maintenance."
Unit_Diag_Bit(72) = "Error in peripherals"
Unit_Diag_Bit_Help(72) = "Check peripherals."
Unit_Diag_Bit(73) = "Electromag interference too high"
Unit_Diag_Bit_Help(73) = "Lower external electromagnetic interference."
Unit_Diag_Bit(74) = "Temperature of medium too high"
Unit_Diag_Bit_Help(74) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(75) = "Ambient temperature too high"
Unit_Diag_Bit_Help(75) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(76) = "Vibration/Impact load too high"
Unit_Diag_Bit_Help(76) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(77) = "Auxiliary power range off-spec"
Unit_Diag_Bit_Help(77) = "Check power supply"
Unit_Diag_Bit(78) = "Auxiliary medium missing"
Unit_Diag_Bit_Help(78) = "Check auxiliary medium."
Unit_Diag_Bit(79) = "Excessive temperature shock"
Unit_Diag_Bit_Help(79) = "Check that the device is operated within its \
specifications."
Unit_Diag_Bit(80) = "Deviation from measurement"
Unit_Diag_Bit_Help(80) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(81) = "Humidity in electronics area"
Unit_Diag_Bit_Help(81) = "Replacement is recommended."
Unit_Diag_Bit(82) = "Medium in electronics area"
Unit_Diag_Bit_Help(82) = "Replacement is recommended."
Unit_Diag_Bit(83) = "Mechanical damage"
Unit_Diag_Bit_Help(83) = "Replacement is recommended."
Unit_Diag_Bit(84) = "Communication error"
Unit_Diag_Bit_Help(84) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
Unit_Diag_Bit(85) = "Foreign material in electro area"
Unit_Diag_Bit_Help(85) = "Replacement is recommended."
;NE107_CONTACT_THERMOMETER (device specific)
Unit_Diag_Bit(104) = "Immersion depth too limited"
Unit_Diag_Bit(105) = "Unequate medium around sensor"
Unit_Diag_Bit(106) = "Temp disturb not representative"
Unit_Diag_Bit(107) = "Inadequate thermal contact"
Unit_Diag_Bit(108) = "Sensor close to heat source/sink"
Unit_Diag_Bit(109) = "External temperature influence"
Unit_Diag_Bit(110) = "Unsufficient thermocupling"
Unit_Diag_Bit(111) = "Thermocoupling too high"
Unit_Diag_Bit(112) = "Friction heat by flowing gases"
Unit_Diag_Bit(113) = "Thermalcapac of sensor too high"
Unit_Diag_Bit(114) = "Deposits"
Unit_Diag_Bit(115) = "Systemrelated resonant vibration"
Unit_Diag_Bit(116) = "Resonantvibrat excited by flow"
Unit_Diag_Bit(117) = "Leakage"
Unit_Diag_Bit(118) = "Abrasion"
Unit_Diag_Bit(119) = "Corrosion"
Unit_Diag_Bit(120) = "Flow approach speed too high"
Unit_Diag_Bit(121) = "Insulation resistant too low"
Unit_Diag_Bit(122) = "Insulation resistant too low"
Unit_Diag_Bit(123) = "Parasitic thermal elements"
Unit_Diag_Bit(124) = "Parasitic galvanic elements"
Unit_Diag_Bit(125) = "Short circuit"
Unit_Diag_Bit(126) = "Shorted coil and break"
Unit_Diag_Bit(127) = "Line/contact resistant too high"
Unit_Diag_Bit(128) = "Compression spring failure"
Unit_Diag_Bit(129) = "Drift of sensor charact curve"
Unit_Diag_Bit(130) = "Insuff contact of meas insert"
Unit_Diag_Bit(131) = "Meas insert mechanical seized"
Unit_Diag_Bit(132) = "Measuring insert in thermowell"
Unit_Diag_Bit(133) = "Measuring insert too short"
Unit_Diag_Bit(134) = "Resistance wire abrasion"
Unit_Diag_Bit(135) = "Mechanic stress character curve"
Unit_Diag_Bit(136) = "Thermal stress character curve"
Unit_Diag_Bit(137) = "Intrinsic heating too severe"
Unit_Diag_Bit(138) = "EMI on measuring circuit"
Unit_Diag_Bit(139) = "Faulty linearisation"
Unit_Diag_Bit(140) = "Incorrect sensor position"
Unit_Diag_Bit(141) = "Faulty comparative point temp"
Unit_Diag_Bit(142) = "Faulty compar of line resistance"
Unit_Diag_Bit(143) = "Unsymmet supply line resistance"
Unit_Diag_Bit(144) = "Wrong material of compens line"
Unit_Diag_Bit(145) = "Damage to supply lines"
Unit_Diag_Bit(146) = "Capacitive feedback"
Unit_Diag_Bit(147) = "Potential transfer"
Unit_Diag_Bit(148) = "Potential differences exceeded"
Unit_Diag_Bit(149) = "Impermiss mix of wire systems"
Unit_Diag_Bit(150) = "Reserve polarity of lines"
Unit_Diag_Bit(151) = "Reserve polarity of RTD lines"
;---------------
UnitDiagType=254
X_Unit_Diag_Bit(35) = "Restart" ;DIA_WARMSTART
X_Unit_Diag_Bit(36) = "Application reset" ;DIA_COLDSTART
X_Unit_Diag_Bit(37) = "Maintenance required" ;DIA_MAINTENANCE
X_Unit_Diag_Bit(40) = "Maintenance alarm" ;DIA_MAINTENANCE_ALARM
X_Unit_Diag_Bit(41) = "Maintenance demanded" ;DIA_MAINTENANCE_DEMANDED
X_Unit_Diag_Bit(42) = "Function check" ;DIA_FUNCTION_CHECK
X_Unit_Diag_Bit(43) = "Out of specification" ;DIA_OUT_OF_SPEC
X_Unit_Diag_Bit(44) = "Parameter update" ;DIA_UPDATE_EVENT
X_Unit_Diag_Bit(55) = "Extension available"
;--- NE107_COMMON
X_Unit_Diag_Bit(56) = "Sensor element exciter faulty"
X_Unit_Diag_Bit_Help(56) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(57) = "Error in evaluation electronics"
X_Unit_Diag_Bit_Help(57) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(58) = "Error in internal energy supply"
X_Unit_Diag_Bit_Help(58) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(59) = "Error in sensor element"
X_Unit_Diag_Bit_Help(59) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(60) = "Error in actuator element"
X_Unit_Diag_Bit_Help(60) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(61) = "Faulty installat e.g. dead space"
X_Unit_Diag_Bit_Help(61) = "Check installation."
X_Unit_Diag_Bit(62) = "Parameter setting error"
X_Unit_Diag_Bit_Help(62) = "Check parameter settings for consistency."
X_Unit_Diag_Bit(63) = "Signal path broken or short cut"
X_Unit_Diag_Bit_Help(63) = "Check signal path."
X_Unit_Diag_Bit(64) = "Overloading"
X_Unit_Diag_Bit_Help(64) = "Check load."
X_Unit_Diag_Bit(65) = "Wrong polarity of aux power"
X_Unit_Diag_Bit_Help(65) = "Check polarity."
X_Unit_Diag_Bit(66) = "Maximum line length exceeded"
X_Unit_Diag_Bit_Help(66) = "Check line length."
X_Unit_Diag_Bit(67) = "Corrosion/abrasion by medium"
X_Unit_Diag_Bit_Help(67) = "Replacement is recommended."
X_Unit_Diag_Bit(68) = "Fouling on sensor element"
X_Unit_Diag_Bit_Help(68) = "Cleaning is recommended."
X_Unit_Diag_Bit(69) = "Auxil medium missing or insuffic"
X_Unit_Diag_Bit_Help(69) = "Check auxiliary medium."
X_Unit_Diag_Bit(70) = "Wear reserve used up (operation)"
X_Unit_Diag_Bit_Help(70) = "Plan maintenance."
X_Unit_Diag_Bit(71) = "Wear reserve used up (wear)"
X_Unit_Diag_Bit_Help(71) = "Plan maintenance."
X_Unit_Diag_Bit(72) = "Error in peripherals"
X_Unit_Diag_Bit_Help(72) = "Check peripherals."
X_Unit_Diag_Bit(73) = "Electromag interference too high"
X_Unit_Diag_Bit_Help(73) = "Lower external electromagnetic interference."
X_Unit_Diag_Bit(74) = "Temperature of medium too high"
X_Unit_Diag_Bit_Help(74) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(75) = "Ambient temperature too high"
X_Unit_Diag_Bit_Help(75) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(76) = "Vibration/Impact load too high"
X_Unit_Diag_Bit_Help(76) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(77) = "Auxiliary power range off-spec"
X_Unit_Diag_Bit_Help(77) = "Check power supply"
X_Unit_Diag_Bit(78) = "Auxiliary medium missing"
X_Unit_Diag_Bit_Help(78) = "Check auxiliary medium."
X_Unit_Diag_Bit(79) = "Excessive temperature shock"
X_Unit_Diag_Bit_Help(79) = "Check that the device is operated within its \
specifications."
X_Unit_Diag_Bit(80) = "Deviation from measurement"
X_Unit_Diag_Bit_Help(80) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(81) = "Humidity in electronics area"
X_Unit_Diag_Bit_Help(81) = "Replacement is recommended."
X_Unit_Diag_Bit(82) = "Medium in electronics area"
X_Unit_Diag_Bit_Help(82) = "Replacement is recommended."
X_Unit_Diag_Bit(83) = "Mechanical damage"
X_Unit_Diag_Bit_Help(83) = "Replacement is recommended."
X_Unit_Diag_Bit(84) = "Communication error"
X_Unit_Diag_Bit_Help(84) = "1. Restart device. 2. Check if failure recurs. \
3. Replacement is recommended."
X_Unit_Diag_Bit(85) = "Foreign material in electro area"
X_Unit_Diag_Bit_Help(85) = "Replacement is recommended."
;NE107_CONTACT_THERMOMETER (device specific)
X_Unit_Diag_Bit(104) = "Immersion depth too limited"
X_Unit_Diag_Bit(105) = "Unequate medium around sensor"
X_Unit_Diag_Bit(106) = "Temp disturb not representative"
X_Unit_Diag_Bit(107) = "Inadequate thermal contact"
X_Unit_Diag_Bit(108) = "Sensor close to heat source/sink"
X_Unit_Diag_Bit(109) = "External temperature influence"
X_Unit_Diag_Bit(110) = "Unsufficient thermocupling"
X_Unit_Diag_Bit(111) = "Thermocoupling too high"
X_Unit_Diag_Bit(112) = "Friction heat by flowing gases"
X_Unit_Diag_Bit(113) = "Thermalcapac of sensor too high"
X_Unit_Diag_Bit(114) = "Deposits"
X_Unit_Diag_Bit(115) = "Systemrelated resonant vibration"
X_Unit_Diag_Bit(116) = "Resonantvibrat excited by flow"
X_Unit_Diag_Bit(117) = "Leakage"
X_Unit_Diag_Bit(118) = "Abrasion"
X_Unit_Diag_Bit(119) = "Corrosion"
X_Unit_Diag_Bit(120) = "Flow approach speed too high"
X_Unit_Diag_Bit(121) = "Insulation resisant too low"
X_Unit_Diag_Bit(122) = "Insulation resisant too low"
X_Unit_Diag_Bit(123) = "Parasitic thermal elements"
X_Unit_Diag_Bit(124) = "Parasitic galvanic elements"
X_Unit_Diag_Bit(125) = "Short circuit"
X_Unit_Diag_Bit(126) = "Shorted coil and break"
X_Unit_Diag_Bit(127) = "Line/contact resistant too high"
X_Unit_Diag_Bit(128) = "Compression spring failure"
X_Unit_Diag_Bit(129) = "Drift of sensor charact curve"
X_Unit_Diag_Bit(130) = "Insuff contact of meas insert"
X_Unit_Diag_Bit(131) = "Meas insert mechanical seized"
X_Unit_Diag_Bit(132) = "Measuring insert in thermowell"
X_Unit_Diag_Bit(133) = "Measuring insert too short"
X_Unit_Diag_Bit(134) = "Resistance wire abrasion"
X_Unit_Diag_Bit(135) = "Mechanic stress character curve"
X_Unit_Diag_Bit(136) = "Thermal stress character curve"
X_Unit_Diag_Bit(137) = "Intrinsic heating too severe"
X_Unit_Diag_Bit(138) = "EMI on measuring circuit"
X_Unit_Diag_Bit(139) = "Faulty linearisation"
X_Unit_Diag_Bit(140) = "Incorrect sensor position"
X_Unit_Diag_Bit(141) = "Faulty comparative point temp"
X_Unit_Diag_Bit(142) = "Faulty compar of line resistance"
X_Unit_Diag_Bit(143) = "Unsymmet supply line resistance"
X_Unit_Diag_Bit(144) = "Wrong material of compens line"
X_Unit_Diag_Bit(145) = "Damage to supply lines"
X_Unit_Diag_Bit(146) = "Capacitive feedback"
X_Unit_Diag_Bit(147) = "Potential transfer"
X_Unit_Diag_Bit(148) = "Potential differences exceeded"
X_Unit_Diag_Bit(149) = "Impermiss mix of wire systems"
X_Unit_Diag_Bit(150) = "Reserve polarity of lines"
X_Unit_Diag_Bit(151) = "Reserve polarity of RTD lines"
EndUnitDiagType
;-------------------------------------------------------------------------
;
;max module text length-----------------"
Module="Not in cyclic data transfer " 0x00 ;Empty module
0
Info_Text="No cyclic data selected for this slot. Function disabled"
EndModule
Module="Conductivity" 0x42,0x84,0x08,0x05
1
EndModule
Module="Temperature" 0x42,0x84,0x08,0x05
2
EndModule
;----------- Description of the module assignment: ---------------------
;
SlotDefinition
Slot(1) = "" 1 1
Slot(2) = "" 2 0,2
EndSlotDefinition